A “Plenum Low Temperature” shutdown alarm is shown on my HMI screen. After I accept this alarm, I cannot clear this alarm by pressing Reset on the plenums page.
Turn the ignition switch off. The CAL temperature controller itself must be reset by momentarily turning off the 120vac supplying it. This may be done by pushing the High Limit and Air Pressure amber lights at the same time for about one second.